UPDATE: 3:00 PM So the Super has granted me permission to attend the School Committee meeting tomorrow night. Gee, that's right up there with "being allowed" to attend a Town Meeting (or root canal).
He attaches a memo from Ronald Bohonowicz explaining that they purposely keep water temperature down in the bathrooms (so I guess they could turn it up if they wanted) and he includes the Uniform State Plumbing Code that restricts temperature to a maximum of 110 but have no minimums.
But the Mass Department of Public Health has the following:
DEPARTMENT OF PUBLIC HEALTH
105 CMR 410.000: MINIMUM STANDARDS OF FITNESS FOR HUMAN HABITATION (STATE SANITARY CODE, CHAPTER II)
410.190: Hot Water
The owner shall provide and maintain in good operating condition the facilities capable of heating water. The owner shall also provide the hot water for use at a temperature of not less than 110°F (43° C) and in a quantity and pressure sufficient to satisfy the ordinary use of all plumbing fixtures which normally need hot water for their proper use and function, unless and to the extent the occupant is required to provide fuel for the operation of the facilities under a written letting agreement. The hot water shall not exceed 130°F (54° C).
The Board of Health agent, Gary Courtemanche visited the school on Friday afternoon (01/09/09) and found the temperature at the Boy's bathroom to be 86.7. At the kitchen sink it was fortunately at 110 and the dish machine washed at 154 and rinsed at 182.
On Jan 12, 2009, at 10:22:27 AM, email@example.com wrote:
Please consider this a formal written request for permission to set
foot on Amherst School property--specifically the Amherst Pelham
Regional High School--to attend the School Committee meeting tomorrow
night January 13 at 7:00 PM where I believe the water temperature issue
at Wildwood Elementary School will be discussed.